T-Project Group, spol. s r.o. signed a contract for the supply of primary and secondary systems DeNOx on the boiler K11 Power Heating Plant in the Ceske Budejovice, Czech Republic. The contract was realized within the project Desulfurization of Power and heating plants Ceske Budejovice, Czech Republic.
August 12, 2014 - Assembly work on the boiler is finishing. Erection of coal burners are continuing according to plan.
September 25, 2014 - Performed a successful boiler pressure test participation TIČR inspection office.
October 1, 2014 - Issue the inspection report according to DIN EN ISO / IEC 17020 (EC unit verification Module G pursuant to Directive 97/23 / EC) and EC issued certificates (TÜV SÜD).
October 15, 2014 - The finish of individual tests on primary systems and initiate the drying of brick insulations.
October 16, 2014 - Start of boiler burners incl.new DENOX system.
November 15, 2015 - T-Project Group, spol. s r.o. signed with the customer The Protocol on the provisional acceptance of the work (PAC) and handed the device to the test operation.
After successful comprehensive test were achieved these guaranteed values:
NOx concentration after the application of primary systems: up to 340 mg / Rm3
Output the NOx concentration after the application of the secondary actions:
up to 200 mg / Rm3
Slippage NH3: 20 mg / Rm3
CO concentration: up to 200 mg / Rm3